Allergan and USFRA have partnered to Refresh the eyes of our Law Enforcement and Fire-Rescue heroes! Contact us for more information on how you can score a donation of Refresh Eye Drops for your firehouse or police station. Join the Refresh America program today!!
PLEASE REVIEW THE USFRA EXTERNAL LINKS POLICY BEFORE SUBMITTING YOUR LINKS.
November 2, 2017 - CPSC has announced a recall of almost 40 million fire extinguishers by Kidde.
This recall involves two styles of Kidde fire extinguishers:
The fire extinguishers can become clogged or require excessive force to discharge and can fail to activate during a fire emergency.
In addition, the nozzle can detach with enough force to pose an impact hazard.
Plastic handle fire extinguishers: The recall involves 134 models of Kidde plastic handle fire extinguishers manufactured between January 1, 1973 and August 15, 2017, including models that were previously recalled in March 2009 and February 2015.
The extinguishers were sold in red, white and silver, and are either ABC- or BC-rated. The model number is printed on the fire extinguisher label. For units produced in 2007 and beyond, the date of manufacture is a 10-digit date code printed on the side of the cylinder, near the bottom. Digits five through nine represent the day and year of manufacture in DDDYY format. Date codes for recalled models manufactured from January 2, 2012 through August 15, 2017 are 00212 through 22717. For units produced before 2007, a date code is not printed on the fire extinguisher.
Push-button Pindicator fire extinguishers: The recall involves 8 models of Kidde Pindicator fire extinguishers manufactured between August 11, 1995 and September 22, 2017. The no-gauge push-button extinguishers were sold in red and white, and with a red or black nozzle. These models were sold primarily for kitchen and personal watercraft applications.
Please visit CPSC.gov to see entire list of 142 models of Kidde fire extinguishers impacted by this recall!
Total # of Units:
About 37.8 million (in addition, 2.7 million in Canada)
The fire extinguishers can become clogged or require excessive force to discharge and can fail to activate during a fire emergency. In addition, the nozzle can detach with enough force to pose an impact hazard.
Consumers should immediately contact Kidde to request a free replacement fire extinguisher and for instructions on returning the recalled unit, as it may not work properly in a fire emergency.
Note: This recall includes fire extinguisher models that were previously recalled in March 2009 and February 2015. Kidde branded fire extinguishers included in these previously announced recalls should also be replaced. All affected model numbers are listed in the charts above.
Recall information for fire extinguishers used in RVs and motor vehicles can be found on NHTSA’s website.
The firm is aware of a 2014 death involving a car fire following a crash. Emergency responders could not get the recalled Kidde fire extinguishers to work. There have been approximately 391 reports of failed or limited activation or nozzle detachment, including the fatality, approximately 16 injuries, including smoke inhalation and minor burns, and approximately 91 reports of property damage.
Menards, Montgomery Ward, Sears, The Home Depot, Walmart and other department, home and hardware stores nationwide, and online at Amazon.com, ShopKidde.com and other online retailers for between $12 and $50 and for about $200 for model XL 5MR. These fire extinguishers were also sold with commercial trucks, recreational vehicles, personal watercraft and boats.
Walter Kidde Portable Equipment Company Inc., of Mebane, N.C.
United States and Mexico
Source: Consumer Product Safety Commission Recall 18-022